Solax Hybrid settings for the new LG Chem 3.3, 6.5 and 10.0 RESU lithium ion battery
On the LG Chem battery set the four DIP switches labelled "SW" under the rubber grommet to:
0 0 1 1
Please also check the other DIP switches and dials are set to the correct positions:
Cell select = 00
TermRes = 11
Can_H = 4
Can_L = 5
GND = 2
The Solax unit should usually detect the battery settings, please check the charge settings are correct.
You will require a crimping tool on site in order to make up the CAT5 communication cable for the battery BMS. This is important as it is the only way to install the communication cable without voiding the LG Chem battery warranty. Please refer to page 22 of the install manual linked below for further information.
We recommend you take a CAT5 tester to site so you can test your cable.
LG Chem RESU Datasheet
LG Chem RESU Install manual
Solax Hybrid Install manual
Solax Portal User guide
Solar Wi-Fi Connection guide
Charge settings for the ZTE Pylontech lithium batteries
Charge settings for the new SolaX 3.3 and SolaX 6.5 lithium batteries
Welcome to the latest innovation from SolarVenti, designers and manufacturers of the greenest ventilation solutions available on the market today - The SolarVenti Heat Recovery Ventilator system or in...
Introducing the new range of Heatese Energy Efficient Boilers designed to save you energy and reduce those bothersome energy bills.
Flighways Business Park
Company Reg: 6849811
Contact 01404 891693